UniMaxx™ Solar Pump Station Booster Pump
How to order?
- Place your order online or contact our office to order directly with the sales team.
- Orders placed online will be confirmed within 24 hours by our order team.
- SunMaxx Solar™ is a manufacturer of solar hot water equipment.
- Availability and production lead-times vary based on our production queue.
Manufacturer Direct Pricing
Please note the referenced prices online are for manufacturer direct pricing only. For wholesale & distribution inquires, please contact our office for an offer.
Want to speak with our office? Call us 1-877-786-6299
Solar Pump Station Booster Pump
List of components
|1) 1½” male union thread|
|2) 1½” union nut|
|3) 3 speeds asynchronous motor inside a housing
(degree of protection : IP44)
Features & Benefits
- 3 different speeds options available
- Two pumps may be used when additional head pressure is needed
- Ideal for small commercial and large residential solar hot water and heating systems
- UniMaxx Pump Skids are built with Wilo Star S30 U25 pumps
- flows up to 30 GPM
- Larger, custom pump systems are available upon request
- Model: Wilo Star S30 U25
- Permissible temperature range: -14°F to 230°F
- Mains connection: 115/120 V, 60 Hz
- Protection class: IP 44
- Threaded connection: 1 1/2”
- Max. operating pressure: 145 PSI
- Power consumption: 1/10 HP
- Max. Amperage: 1.08A
- Pump housing: Grey cast-iron
- Impeller: Polypropylene
- Shaft: Stainless steel insulation – EPP
- Fittings: Brass
- Seals: Viton/teflon
- Bearing: Carbon
Below, the pressure drop characteristic of UNIMAXX-PLUS-SC-S30-R solar pump, which is the heart of the solar hot water pumping system, is presented:
SunMaxx’s Pump Stations are an all in one solar hot water component featuring a circulator pump, a digital controller and valves engineered to keep your system circulating the solar heat transfer fluid through the collectors and into the storage tank.
SunMaxx will size a pump station specific to your needs. No need to do the math!!!
Our pump station’s fill valve has GHT hose threads on the outside. You can easily make an adaptor using the following three fittings, which can be purchased at your local hardware store or plumbing supply.
- Schrader valve x ¼” male NPT
- Reducing Bushing, ½” NPT Male x ¼” NPT Female
- Hose fitting, ½” NPT male x ¾” swivel GHT female
Use Teflon tape on the NPT threads of the Schrader valve and bushing in constructing the adaptor. When attaching the adaptor to the pump station, be sure to use two tools: one to hold the fill valve in place, and one to tighten the adaptor. That way, you won’t create leaks in the pump station itself while testing.
Take a deep breath and let all your air out… of your Solar thermal system One of the biggest issues with a successful commissioning is air removal. Any time you spend with this detail will be time well spent. Air pockets become entrained within your HTF and like to find places to hide. Air pockets can form between your HTF and the inner wall of piping (especially with flexible piping) and can only be removed through persistence and time. Here are a few things you can do to help this process. First, be sure that your air purger is located on the high and hot side of your collector series. The hotter the fluid the less the ability for dissolved gasses to stay in solution and the higher the air vent, the more likely you will effectively remove trapped air that, due to its buoyancy, will rise to the top. Once you feel most of the air has been removed this way, you can shut that air eliminator off or remove it all together. If you install a Titan Power Plus collector, you will have a manual air bleeder permanently installed in your line set connections. If you install a ThermoPower collector, you will include an air vent that should be isolated and de-commissioned at this point. Now, down to the pump station. The UniMaxx pump stations have an integral air eliminator with a scoop that will allow entrained air to collect and be bled off manually by opening the valve up to a full turn until HTF comes out. This can be done each day for the first few days or periodically checked. Smaller systems will take much less time removing the air. Another way of enabling the removal of air is to run the pump at maximum speed during commissioning, this will help to break the friction that holds the bubbles to the inner wall thus forcing the bubble through and out. After words, you should adjust your pump speed accordingly. If air persists in your system, it will inevitably find its way to the suction side of your pump and cause cavitation and eventual pump failure. If your pump appears to be not pumping, it is likely that although it is receiving 115v, it cannot pump because of air pockets. Simply unplug your pump and manual override and give it a few minutes. Air will work its way out, pump can run and then you need to go back to the air purging steps. Please view our SunMaxx technical manual (linked) for further instruction in effective system commissioning.
Solar Pump Stations
How to Order:
If you are confident with your solar hot water heating requirements you can place your order online by clicking on the add to cart button which is located above. All orders are reviewed by our solar hot water heating department and the customers are contacted in order to ensure that you have ordered the correct merchandise for your application. In the event you have any questions our sales staff are available from 8:30AM to 5:30PM EST.
Silicon Solar Inc ships products internationally please ask your sales representative for a shipping rate to your destination.
If you have questions need help or simply feel uncomfortable placing your order online feel free to contact the product representative at 1-800-786-0329.