How can I connect an air compressor to my pump station to pressure test my solar thermal system for leaks?Arun base
How can I connect an air compressor to my pump station to pressure test my solar thermal system for leaks?
Our pump station’s fill valve has GHT hose threads on the outside. You can easily make an adaptor using the following three fittings, which can be purchased at your local hardware store or plumbing supply.
- Schrader valve x ¼” male NPT
- Reducing Bushing, ½” NPT Male x ¼” NPT Female
- Hose fitting, ½” NPT male x ¾” swivel GHT female
Use Teflon tape on the NPT threads of the Schrader valve and bushing in constructing the adaptor. When attaching the adaptor to the pump station, be sure to use two tools: one to hold the fill valve in place, and one to tighten the adaptor. That way, you won’t create leaks in the pump station itself while testing.